Exterior/interior ventilators for window frames
Kitchen, bathroom,and WC extraction
Airflow circuit components
Integrated airflowcontrol modules
Air intakes and outlets
Foul air outletroof components
Natural ventilation grilles
Exterior facadeair intake grilles
The M self-regulating air inlet fitted indoors is made from polystyrene. It can be fitted with a GAM insect screen and accepts a CG-M grille/cap. For installation in main rooms (living and bedroom) to supply air renewal in single flowrate forced ventilation systems.
Available in flowrates of 15, 22, 30, or 45m³/h. The 15m³/h air inlet provides additional flowrates of 22 or 30 m³/h and the 22 m³/h allows up to 30 m³/h.
It works both on vertical walls and on inclined planes (e.g., roof skylights, undersides of roller shutter boxes).
The cowl for fitting to the external wall is made from UV- and weather-resistant polystyrene in the same colours as the air inlets (except facade grille GAE2A made from aluminium).
Exclusively for fitting to surfaces sheltered from bad weather. For non-sheltered surfaces please enquire with us.
On the inside, the air inlet is centred on the 341 x 12mm slot and held in place by 2 screws.
The cowl or grille on the external wall is centred on the slot and held in place by 3 screws (horizontally fitted cap).
GAM insect screens must not be used if the model M is fitted with the CG-M cap or is used in conjunction with grilles GPE2A and GAE2A.
The components must be kept easily accessible for cleaning and maintenance.
M-G 15/22/30 m³/h air inlets: the inlet airflow rate is determined by the snap-off tabs (marked 15, 22, and 30) on the two regulator bar holding clips. The lowest remaining value indicates the flowrate.
The 15m³/h model can also be modified in-situ to provide flowrates of flowrates of 22 or 30 m³/h by carefully breaking off the relevant snap-off tabs. Break the 2 tabs marked 15 to obtain 22m³/h and the 2 tabs marked 22 to obtain 30 m³/h.
The 22m³/h model can also be modified in-situ to provide a flowrate of 30 m³/h by carefully breaking off the relevant snap-off tabs. Break the 2 tabs marked 22 to obtain 30 m³/h.
M-G 45m³/h air inlet: the inlet airflow rate is found on the two retaining clips of the regulator bar (marking 45).